Service of combi boiler and replacement of 2 mixer taps.
Very thorough service of boiler and also checked the gas supply which revealed a gas leak at the meter. Pete contacted emergency gas services who replaced the faulty parts. Pete did an excellent job of removing the existing taps which is always a difficult task and ensured there were no leaks when he had fitted the new taps. Would have no hesitation in recommending.
ST LEONARDS CUSTOMER
Carbon Monoxide Test.
As soon as my carbon monoxide alarm near my boiler went off there was only one person I had in mind for the job. Friendly Pete was there for me yet again to reassure and to assist. He explained what he would do in simple terms and had all the detection equipment to get the job done. He arranged the appointment and carried out the work within 2 hours of me 1st calling him. Pete I now have you on speed dial for the future!! Thanks again I can’t thank you enough. ;-))